We are sending an Integration command to turn ON a light. It is turning ON and then OFF. We see this problem in 7.5 and 7.6. We did not have it earlier versions. If we revert back to an earlier (7.1) version, the problem is not manifested.
Please see the messages sent and received.
I’m sending an ON (DimTo 100) command to device 7, a lava lamp:
Tue Jul 08 10:41:46 PM Sent: #OUTPUT,7,1,100
Tue Jul 08 10:41:46 PM Rcvd: ~OUTPUT,7,1,100.00
Tue Jul 08 10:41:46 PM DimTo 100.00' (R110) LavaLamp (Direct Command)
The string I get back (~OUTPUT,7,1,100.00) is verifying that device 7 was set (1) to level (100.00). This is what I expected.
But here’s an additional message that is throwing things off:
Tue Jul 08 10:41:46 PM Rcvd: ~OUTPUT,7,29,0
Tue Jul 08 10:41:46 PM DimTo 0' (R110) LavaLamp (External Command)
I’m interpreting that as device 7 is going to level 0. The ‘29’ is an unknown ‘action’ from Lutron that is not documented in the latest protocol doc (revision ‘O’).