Originally Posted by stevi
I'm assuming you are using the QSNE modules for remote zone programming which is a great feature, the amount of QSNE modules you can use depends on how many Grafik Eye Zones there are for example.
One QSGR-6### could theoretically control 6 QSNE zones, This could also be any combination
Zone 1 - Remote Dim - QSNE-4T10-D
Zone 2 - Remote Dim - QSNE-4A-D
Zone 3 - Remote Digital -QSNE-2ECO-D
Zone 4 - Remote Digital -QSNE-2DAL-D
Zone 5 - Remote Non-Dim -QSNE-4S10-D
Zone 6 - Remote Dim - QSNE-4A-D
The only "rule" to follow is it is a one to one zone stealing scenario, if you want a 0-10v zone off your Grafik Eye you will sacrifice that zones phase dimming capability. It's really easy to do and I recommend it a lot to my customers in mixed load Grafik Eye jobs.